Call 0141 432 0001 now for your free no obligation quote or click the button for our contact information.
Legionella Control (HSE)
Get a quote
Temperature control is the primary method used to control the risk from Legionella.
Water services must be managed and controlled at suitable temperatures that will prevent Legionella Proliferation (growth) such as:
- Hot water storage cylinders (calorifiers) should store water at 60°C or higher
- Hot water should be distributed at 50°C or higher
- Cold water should be stored and distributed below 20°C.
- Thermostatic mixer valves (TMV) need to be fitted within 1.5 metres of the outlet it supplies.
Your Legionella Control (HSE) manager should frequently inspect, monitor and maintain the water system, in accordance with the site risk assessment.
Sentinel outlets (nearest and furthest to stored hot and/or cold water) should be identified so that monthly checks of distribution temperatures can be carried out. Stored hot water temperatures should also be checked and reviewed every month and stored cold water tank temperatures at least every six months.
As stagnant water provide Legionella bacteria an ideal environment for growth, dead legs/dead ends in pipe-work should be removed. Infrequently used outlets, (especially aerosol generating outlets such as showerheads) should be flushed on a weekly basis. All outlets that generate a spray (showers and spray taps) should be cleaned and descaled on a quarterly basis. Cold-water storage tanks should be cleaned periodically and all water should be drained from hot water cylinders to check for debris or corrosion.
Water sample analysis can be used as an additional control method for systems that are presenting temperatures out with the control parameters.
I’ve been told that, by law, I must have my portable electrical appliances tested every year. Is this correct?
The Electricity at Work Regulations 1989 require that any electrical equipment that has the potential to cause injury is maintained in a safe condition. However, the Regulations do not specify what needs to be done, by whom or how frequently (ie they don’t make inspection or testing of electrical appliances a legal requirement, nor do they make it a legal requirement to undertake this annually).find out more